Silver TA is a wired room thermostat. The user can adjust the room thermostat with the requirement temperature and get more comfortable and economic heating.
- Sensitive temperature measuring
- Heating calibration
- ON/OFF Control
- Wired Connection
DECLARATION OF CONFORMITY
Compatible Directives: Electromagnetic Compatibility Regulation 2014/30/EU (EMC EN 61000-6-3: 2007 + A1: 2011, EN 61000-6-1: 2007 Low Voltage Directive 2014/35/EU (LVD EN 60730-2-9:2010, EN 60730-1:2011)
Power supply 3 Vdc (2 x AAA alkaline battery)
Battery life 1 Year (2 x AAA)
Maximum capacity of the contacts 2A (30 Vdc)
Temperature display range -10°÷50°C
Temperature regulation range 5°÷30°C
Temperature resolution 0,5°C
Storage temperature -20°÷60°C
Temperature precision 0,1°C
Dimensions 88mm / 136mm / 34mm
Thermostat control keys
ROOM THERMOSTAT PLACEMENT
Place your room thermostat in a room where you most use it as your
living area. For example: living room. Avoid installing the room
thermostat where there is a lot of air circulation such as door entry or
window edges. Also, do not place in places near heat units (central
heating system, fireplace, etc.) and places that receive direct
sunlight. We recommend that the room thermostat be placed at an
altitude of 50 cm to 150 cm from the floor. You can try a few places to
find the most suitable place.
Remove your room thermostat from Wall hanger. Then remove the battery housing from the back side of thermostat. Install 2 alkaline batteries to battery housing. Please be sure the directions of batteries. Hang your thermostat on the Wall hanger after assemble battery housing back. Change the both batteries together.
When the product is not used for a long time (more than 15 days), remove the batteries. Otherwise, malfunctions that will occur are out of warranty.
Please throw away dead batteries to trashes special only for batteries.
ROOM THERMOSTAT WIRING DIAGRAM
Only persons who have got Professional Competence should make operations electric wiring or boiler setup.
Description of controls and operation
ROOM THERMOSTAT HEATING CALIBRATION
Temperature sensors which are used for room thermostats, are very sensitive. No other thermometers in your living area have that sensitivity. You can calibrate your room thermostat if you would like to get the temperature of the other thermometers in your living space.
- Press the button for 3 seconds when the device is off.
- In order to see the desired temperature, set the temperature difference by turning the button to right or left. This value can be set between -8° and +8°.
- Exit the menu by pressing the button.
Note: Recommended temperature calibration is “0.0°C”.